EnergyHub XL cabinets must be placed on a hard, flat floor in a weather-protected space free of condensation. Also keep in mind that it must be accessible for possible service. See also installation manual.
Each EnergyHub XL module in a EnergyHub cabinet generates a heat load of up to approx. 700 W at maximum power. It should therefore be placed in a room with an air exchange of at least 80 l / s per XL module or a room with cooling. Note that during solar production, the maximum heat load occurs only for a few hours in the middle of the day during the summer, which is why the average heat load to the building over a day is significantly lower. If EnergyHub is placed in large rooms, the ventilation requirements can therefore be reduced.